First and Foremost, Co Sensor Calibration is a safety requirement when managing or owning buildings, Commercial, Residential, or Industrial.
Any Property which has a car park, without satisfactory natural ventilation, must ventilate the car park via mechanical means.
The Occupational Safety and Health Act, section 21, Ensures any Carbon monoxide-controlled ventilation system is regularly serviced, and records kept, ensuring CO levels do not exceed exposure standards. Carbon monoxide sensor test & calibration is an essential service.
Carbon Monoxide is a poisonous gas which is created when burning gasoline, wood, propane, charcoal or other fuel. It is a colourless, odorless, tasteless gas. Which is why you need specialized detectors and an extraction system.
In a nutshell, the gas sensor detects the gas (via a device which actually delipidates over time, hence the regular calibration) and sends a signal (4 – 20 Milliamp or 0- 10 volts DC) to a car park fan system controller.
The Controller will then start fans and if a Variable speed drive is detected, the controller will increase the speed of the fans subject to the amount of gas sensed and the set point of the controller
Typically, the Controller with have a start set point of around 8 ppm (parts per million) to start the fans, the fans will run for a minimum of 4 minutes. At 24 ppm the system and / or the fans should be 100%.
The sensor must detect zero ppm for at least 4 minutes, and the system has run for a minimum of 7 minutes, before the fans are allowed to deactivate.
An Alarm for high Co Concertation will be Annunciated at 35 ppm after 1 minute
The VSW is used primarily to conserve energy, it creates a “soft start scenario for the fans reducing the current draw as compared to D.O.L (Direct on Line)
D.O.L will draw around three times the nominal run current at start up.
The VSD means less current draw and less wear and tear on the mechanical component of the fan.
It also means the fan may not have to reach 100% before all the Carbon Monoxide is ventilated out of the car park and the sensor returns to Zero.
This provide an Energy saving also.
AS1668.2.-1991 section 4
As a company whom service Fire systems, Mechanical HVAC systems and electrical we offer this service, Co Sensor Calibration, as part of package or individually.
The Mechanical ventilation component (fans and duct etc) and the electrical Component (Controller, Switchboard and mains Power) and the fire system (the FIP will send a trip signal to the Mechanical Ventilation Switchboard when in Fire Mode) all link with the Car park ventilation system.
We are CM3 Prequaified trade based company providing Mechanical services, Electrical Services, Fire and Automation (BMS)
Below is a service request form, tell us about your situation and what you need. We’ll get back to you typically in a couple of hours or the next business day
Operations Strategy in Commercial Buildings One Operations Strategy in Commercial Buildings that will make your day better in Facility Management This is a simple operations strategy, when engaging vendors, suppliers, and contractors, in commercial and residential buildings, can make facility management easier. Operations Strategy in Commercial Property The fundamental suppliers, who work for or within […]
A Fire & HVAC Maintenance Short Cut to Avoid An uncomfortable conversation. A little bit about us We look after buildings, be they residential strata apartment blocks, Commercial, Retail, industrial, CBD Hotels, Clubs, and so forth. Our Prime core business is in the trades and technical services, in particular Fire protection services, HVAC Mechanical Services, […]
Building Recommissioning Improving Building Overall Performance. When do we need to perform building recommissioning?What will it achieve?What is the cost?How thorough should we be? What is Building Recommissioning? Why would we need to recommission our Building When a building is commissioned at the end of construction, the D.L.P, (Defects Liability Period) will typically begin, that […]
Negating the “Management by Crisis” Scenario! Mitagating Reactive Management with Technology, that is, Intelligent Buildings. Typically, Management by Crisis or Reactive management, is a result of lack of resources, every industry manager has had the experience and every manager looks forward to the crisis coming to a swift and economic conclusion. So how do we […]
Do you keep an Asset Register Database for your building? Creating and Maintaining an Asset register is not always on the priority list of the facility manager, but, it’s a good indication as to the work load the manager has, and if there is time enough to maintain some sort of asset register. The register […]
Pneumatic Controls Building Management Systems – Pneumatic Controls Popular back in the 1970’s and 1980’s, major concerns like Honeywell and Johnson Controls had many projects supplied with Pneumatic Controls, some or at least parts are still in service, especially damper and valve actuators. Optimizing the torque in these actuators via an “E to P” device. […]
Sick Building Syndrome Building Management System Is your building “unwell”? What is it? and does a “sick building” cost the landlord money directly and indirectly? We read about “Sick Building Syndrome” from time to time, in various publications, and we ask “what is the cost?”. The Cost to the Landlord, The Cost to the Property […]
Building Management System Giving you Grief Unlock Your Building from “BMS Single Vendor Captivity”. Building Management Systems (BMS) was designed as labour and energy-saving systems. They can be an absolute delight to work with, delivering information accurately, switching plant equipment, lighting, and monitoring other building services. Recording and trend logging the results the physical assets […]
Energy Conservation Dependence on Maintenance. Building Intelligence, Mechanical Services, Automation, Fire and Electrical. Energy conservation and Maintenance are all co-dependent. Maintenance Services Proper Maintenance of building services aligned with energy measurement and control, provides a mutually beneficial environment for the commercial building. The energy conservation dependence on maintenance of building services and systems can not […]