First and Foremost, Co Sensor Calibration is a safety requirement when managing or owning buildings, Commercial, Residential, or Industrial.
Any Property which has a car park, without satisfactory natural ventilation, must ventilate the car park via mechanical means.
The Occupational Safety and Health Act, section 21, Ensures any Carbon monoxide-controlled ventilation system is regularly serviced, and records kept, ensuring CO levels do not exceed exposure standards. Carbon monoxide sensor test & calibration is an essential service.
Carbon Monoxide is a poisonous gas which is created when burning gasoline, wood, propane, charcoal or other fuel. It is a colourless, odorless, tasteless gas. Which is why you need specialized detectors and an extraction system.
In a nutshell, the gas sensor detects the gas (via a device which actually delipidates over time, hence the regular calibration) and sends a signal (4 – 20 Milliamp or 0- 10 volts DC) to a car park fan system controller.
The Controller will then start fans and if a Variable speed drive is detected, the controller will increase the speed of the fans subject to the amount of gas sensed and the set point of the controller
Typically, the Controller with have a start set point of around 8 ppm (parts per million) to start the fans, the fans will run for a minimum of 4 minutes. At 24 ppm the system and / or the fans should be 100%.
The sensor must detect zero ppm for at least 4 minutes, and the system has run for a minimum of 7 minutes, before the fans are allowed to deactivate.
An Alarm for high Co Concertation will be Annunciated at 35 ppm after 1 minute
The VSW is used primarily to conserve energy, it creates a “soft start scenario for the fans reducing the current draw as compared to D.O.L (Direct on Line)
D.O.L will draw around three times the nominal run current at start up.
The VSD means less current draw and less wear and tear on the mechanical component of the fan.
It also means the fan may not have to reach 100% before all the Carbon Monoxide is ventilated out of the car park and the sensor returns to Zero.
This provide an Energy saving also.
AS1668.2.-1991 section 4
As a company whom service Fire systems, Mechanical HVAC systems and electrical we offer this service, Co Sensor Calibration, as part of package or individually.
The Mechanical ventilation component (fans and duct etc) and the electrical Component (Controller, Switchboard and mains Power) and the fire system (the FIP will send a trip signal to the Mechanical Ventilation Switchboard when in Fire Mode) all link with the Car park ventilation system.
We are CM3 Prequaified trade based company providing Mechanical services, Electrical Services, Fire and Automation (BMS)
Below is a service request form, tell us about your situation and what you need. We’ll get back to you typically in a couple of hours or the next business day
Ensuring Compliant water storage methods in Commercial buildings The Responsibility At some point in time, it will occur that an owner/occupier or manager will be confronted by a requirement from an external regulatory body for compliance regarding compliance of various water system components. Not everyone is aware of the components requiring legislative compliance until they […]
Is the Landlord Always Right? The Landlord is keen to protect his Nabers investment in the assessment rating of their building, and so they should; but at what cost, especially, when the foundations and protocols of the Nabers assessment are not fully understood by either party negotiating the commercial lease, consequently clouding the process. Tenant […]
We Found ourselves in a situation where we had to terminate a vendor | What are your thoughts? Let us set the Scene. Residential apartment block, common basement of three levels, 7 towers, total of 182 apartments. Circa 6 years old An Air conditioning contractor whom looks after the water treatment, the chiller, and associated […]
Negating the “Management by Crisis” Scenario! Experienced Managers Know this Expression. Typically, a result of lack of resources, every industry manager has had the experience and every manager looks forward to the crisis coming to a swift and economic conclusion. So how do we avoid or reduce the occurrence of situations which envelop us, sometimes […]
Contract Management Clauses Contract Management gone wrong: There many strategies involved in contract management which pursue outcomes aligned with goals and objectives. In recent months, we have found ourselves bidding for various Facility Management and Services opportunities to find the business at the “top of the tree”, wanting to split and split contracts. The division […]
Can you use Social media in Building Management? Whether Social Media is your “thing”; it is here to stay Social Media is definitely not my thing, writing a public notice that I had Weeties for breakfast and forgot to put the cat out is not entirely in my comfort zone, however, there is no escaping […]
A Contract Management Fail An outline of this privileged observation: Contract Management Fail: In a nut shell, a HVAC contractor is a given a task to replace a Fan Coil Unit (FCU). The contractor submitted his price, received the order and began the job. He didn’t consult with any other trades, tenancies or technicians involved […]
Outsourcing Facility Services Facility Services delivery includes more than just attending site and organizing corrective maintenance, it encompasses many solid attributes of good business and the foundation of many long term business relationships, for example: communications, transparency, trust, accountability, reporting Mile stones Key Performance Indicators just to name a few These all form part […]
Pest Control Pigeons Are Pigeons leaving unsightly droppings on your building and car park pipes, ledges, and facades? Have the pigeons damaged your property? Is the property devalued or less inviting as a result? What are you doing about it? Pigeons find favorite places to nest in Commercial buildings, residential apartment buildings, warehouses, industrial; there […]